SDR nedir ve borunun basınç derecelendirmesini nasıl etkiler?
The SDR is the ‘Standard Dimensional Ratio' and refers to the geometry of the pipe. SDR is defined as the ratio of the nominal outside diameter to the nominal wall thickness.
SDR = dn/en
- dn is the nominal outside diameter of the pipe
- en is the nominal (minimum) wall thickness of the pipe
Therefore a higher SDR indicates a thinner-walled pipe at any given diameter.
The relationship between the SDR and the pressure rating is given by Lames formula for the hoop stress in thick wall cylinders:
s = P(dn - en) / 2 en
This can be rearranged as;
s = P (SDR - 1) / 2
- s is the maximum hoop stress
- P is the internal pipe pressure
The hoop stress is the design stress for the material, which is the (MRS) divided by the overall service (design) coefficient C.
MRS/C = P (SDR - 1) / 2
P = 2 MRS / C (SDR - 1)
This pressure ‘P' is then defined as the ‘Maximum Operating Pressure' MOP, or the pressure rating of the pipe.
MOP = 2 MRS / C (SDR - 1)
- MRS and MOP are in MPa
MOP = 20 MRS / C (SDR - 1)
- MRS is in MPa
- MOP is in bar.
Example ; What is the MOP or pressure rating of an SDR11 PE100 water pipe?
For PE100 the MRS = 10 MPa. For water applications the minimum recommended service design coefficient ‘C' is 1.25.
MOP = 20 * 10 / 1.25 (11 - 1)
MOP = 16 bar
The following Table shows the range of available SDRs in PE100 pipe.
|SDR||Available to Order||Readily Commercially Available|